Oxygen 93 Percent
» Oxygen 93 Percent is Oxygen produced from air by the molecular sieve process. It contains not less than 90.0 percent and not more than 96.0 percent, by volume, of O2, the remainder consisting mostly of argon and nitrogen.
Packaging and storage Preserve in cylinders or in a low pressure collecting tank. Containers used for Oxygen 93 Percent must not be treated with any toxic, sleep-inducing, or narcosis-producing compounds, and must not be treated with any compound that will be irritating to the respiratory tract when the Oxygen 93 Percent is used.
Labeling Where it is piped directly from the collecting tank to the point of use, label each outlet Oxygen 93 Percent.
noteThe various detector tubes called for in the respective tests are listed under Reagents in the section Reagents, Indicators, and Solutions.
Where it is preserved in cylinders, reduce the pressure by means of a regulator. Measure the gases with a gas volume meter downstream from the detector tube in order to minimize contamination or change of the specimens.
A: When tested as directed in the Assay, not more than 10.0 mL and not less than 4.0 mL of gas remains.
B: Pass 100 ± 5 mL released from the vapor phase of the contents of the Oxygen 93 Percent container or from the outlet at the point of use through a carbon dioxide detector tube at the rate specified for the tube: no color change is observed (distinction from carbon dioxide).
Odor Carefully open the container valve or system outlet to produce a moderate flow of gas. Do not direct the gas stream toward the face, but deflect a portion of the stream toward the nose: no appreciable odor is discernible.
Carbon dioxide Pass 1000 ± 50 mL through a carbon dioxide detector tube at the rate specified for the tube: the indicator change corresponds to not more than 0.03%.
Carbon monoxide Pass 1000 ± 50 mL through a carbon monoxide detector tube at the rate specified for the tube: the indicator change corresponds to not more than 0.001%.
Assay Place a sufficient quantity of ammonium chloride-ammonium hydroxide solution, prepared by mixing equal volumes of water and ammonium hydroxide and saturating with ammonium chloride at room temperature, in a test apparatus composed of a calibrated 100-mL buret, provided with a two-way stopcock, a gas absorption pipet, and a leveling bulb, both of suitable capacity and all suitably interconnected. Fill the gas absorption pipet with metallic copper in the form of wire coils, wire mesh, or other suitable configuration. Eliminate all gas bubbles from the liquid in the test apparatus. Activate the test solution by performing two or three tests that are not for record purposes. Fill the calibrated buret, all interconnecting tubing, both stopcock openings, and the intake tube with liquid. Draw 100.0 mL of Oxygen 93 Percent into the buret by lowering the leveling bulb. Open the stopcock to the absorption pipet, and force the Oxygen 93 Percent into the absorption pipet by raising the leveling bulb. Agitate the pipet to provide frequent and intimate contact of the liquid, gas, and copper. Continue agitation until no further diminution in volume occurs. Draw the residual gas back into the calibrated buret, and measure its volume: not more than 10.0 mL and not less than 4.0 mL of gas remains.
Auxiliary Information Please check for your question in the FAQs before contacting USP.Chromatographic Column
USP32NF27 Page 3173Pharmacopeial Forum: Volume No. 31(4) Page 1107
Chromatographic columns text is not derived from, and not part of, USP 32 or NF 27.